|Place of Origin:||ShenZhen|
|Minimum Order Quantity:||1set|
|Packaging Details:||Carton packing for one sets, one set including three piece with Components|
|Delivery Time:||Within 7 days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||36,000,00pcs per year|
|Type:||Sensor Split Core Current Transformer||Feature:||Easy Assembly|
|Usage:||Protection For Strong Mobility||Application:||Space-constrained Or Uninterrupted Power Systems.|
|Installation Site:||Outdoor||Characteristic:||Easy Assembly|
split core ac current sensor,
split core current transducer
100A 50/60Hz Sensor Split Core Current Transformer DC/AC Current Transformer
"SCVTX-0.72W" type with voltage contact function split core CT is designed for assembly to the existing main line or cable electrical installation without cut off the line.Its secondary output is standard current signal of 5A or 1A to match the input port requirement of energy meter, monitoring and control terminal. It is applicable for energy meter, distribution cabinet, control switchgear and other power monitoring and control equipment. Puncturing voltage sensor, through the conductive needle puncture to the measured wire, directly connect with conductor, thereby collecting the voltage signal in the transmission line.
|Highest equipment voltage||V||720V|
|Power frequency withstand voltage||kV/S||3kV/60S|
|Rated primary current||A||100-3000A|
|Rated Secondary current||A||5A,1A||Cutomized are available, mA|
|Rated continuous thermal current||1.2lmax|
|Standard: GB 20840,GB 4208-2008,IEC/EN 61869JEEE C57.133.3JEC 60529|
Protection level : IP65；
Easy assembly,no need to cut off cable causing power outage.
Split core CT is locked by lead sealed screw to prevent from unauthorized operation.
Designed with split core, ring type structure,with voltage contact function.
Energy meter, Switchgear, Smart grid,
Power Measurement and Control Management System
General measurement and protection for strong mobility or space-constrained or uninterrupted power systems.
Power instrumentation, electronic multi-function energy meter and field calibrator, instrumentation measurement and protection.
1. Primary current direction should be as per the arrow in CT case.
2. Primary conductor temperature not more than 1000C
3. When primary conductor fully occupy the CT hole, then performance of di/dt and response time are the best
Contact Person: Isabel